- The unit is intermittently welded and caulked with an rtv sealant.
- The unit shall be manufactured from 12 ga. And 14 ga. Galvanized steel, t-304 stainless steel, t-316 stainless steel or aluminized steel material.
- Star knobs and studs shall be used to retain doors.
- A neoprene gasket shall seal the door edges to the enclosure.
- Unit comes equipped with a removable locking tray mechanism for gasket or fluid seal filters.
- all hepa filters shall seal on the downstream side of the unit.
- Unit is designed to accommodate standard and custom size prefilters, hepa filters and carbon filters
Call For Pricing